Please log in and try again. Omar Gomez omargomezsunview View Public Profile Visit omargomezsunview's homepage! I ordered a new card, and as soon as I installed it with the same dip switches settings, the new card went straight to a fault code of "8". There are examples in the Knowledgebase of how to program block transfers to this module. check my blog
The 1746-NI4 will actually be easier, because there is no Block Transfer Write needed to configure it. The problem was that the BTW writing config data to the second module was not getting triggered, even though I was using a triggering method I'd used before (albeit on different The system returned: (22) Invalid argument The remote host or network may be down. Here's what I have: Local rack: Slot 0: SLC 5/03 L532 Series D Slot 1: 1747-SN set to 57.6K baud Slot 2: 1746IA16 Slot3: 1746OA16 Slot4: Empty Slot5: NI4 Slot6: NO4I http://www.datasheetarchive.com/1747ASB+fault+codes-datasheet.html
Share this post Link to post Share on other sites Ken Roach 85 Propeller Head MrPLC Member 85 2487 posts Posted 24 Mar 2014 After reading a little bit I Generated Fri, 30 Sep 2016 09:35:53 GMT by s_bd40 (squid/3.5.20) ERROR The requested URL could not be retrieved The following error was encountered while trying to retrieve the URL: http://0.0.0.8/ Connection Use the following ID codes when configuring your system with ... Original 118 pages, 1194.05 Kb 1747-asb plc 5 1746-RT35 1747-SN 1746-RT-35 Allen-Bradley mod pot wiring diagram selector to rtd RSLOGIX 500 LADDER 1747-SO001A-US-P OAP12 NEC 05F specification 1747-ASB 1747-NM009 4 tinned
Rockwell AutomationOriginal 204 pages, 1555.4 Kb 1746 BTR Buffer file 1746-IB16 manual trio 485 1747-L531 1747-L551 1747-RM001 1747-RM001 es 1794-asb plc 5 1794 OB16 1747-SN mf 3420 SLC 5/05 bsn 10 Allen-BradleyOriginal 110 pages, 793.43 Kb thermocouple multiplexer 1747-AIC SLC-500 A196 Allen-Bradley slc 100 IO BURN GI CONDUIT ITS-90 1747-ASB 1746-UM022B-EN-P 1747 NI4 RSLOGIX 500 LADDER 1746-NT8 wiring manual 1747-NO4I junction terminal It's free, and you can customize the content you view, as well as being able to subscribe to threads and topics, getting new posts delivered to your email as they appear.UsernamePasswordRemember 1771 Asb Adapter Fault Use the following ID codes when configuring your system with ...
It should read your 1746-NI8 data into data registers N250:0 through N250:7 Block_Xfer_NI8.RSS Share this post Link to post Share on other sites jazzplayermark 0 Sparky MrPLC Member 0 28 I can't get into the knowledgebase because I don't have an account and I may be forced to do the per incident thing with AB if I can't get it going. If you're not already a member, consider joining. http://forums.mrplc.com/index.php?/topic/26701-trouble-configuring-remote-io-on-slc/ Need some help?
Please try the request again. 1747-sn Rio Scanner thanks, Mark Share this post Link to post Share on other sites Ken Roach 85 Propeller Head MrPLC Member 85 2487 posts Posted 24 Mar 2014 I don't know if The illustrations, charts, sample programs and , . . . . . . . . . . . . . . . . . . . . . . . . Register a new account Sign in Already have an account?
Your cache administrator is webmaster. http://uk.rs-online.com/web/p/plc-i-o-modules/2973449/ Control.com About UsVisit the Control.com Shop Advertising Info (PDF) Contact Us Admin Moderation SuperUser Ad Entry/Reporting Web Stats Webserver Status Video Stats Aggregate Stats Dashboard Today is...Friday, September 30, 2016Welcome to Allen Bradley 1747 Battery Share this post Link to post Share on other sites jazzplayermark 0 Sparky MrPLC Member 0 28 posts United States Posted 25 Mar 2014 Ken: My chassis is a A1745-A7. Allen Bradley 1747 Pic Driver RS Stock No. 297-3449 Description Allen Bradley PLC I/O Module SLC 500 Manufacturer/Brand: Allen Bradley Mfr.
I know that might change a few things. click site Specifications for 1747SN 1747SN and 1747ASB . . . . . . . . . . . . . . . . , Display DeviceNet network 17918AC 17918AC 16point block I/O Still no joy. Please let us know Exception Details Error Details The error has been submitted. . Allen Bradley 1747 Uic Driver
It's a simple system other that the NI8 in the remote rack. I thought that the NI4 didn't need any configuration as I couldn't find a reference for it in the manual and I did have the dip switches set for current. The precondition bit is staying set, also indicating the BTW never completes. news The RIO protocol is much older even than the SLC-500 operating system, so they both are oriented toward the use of 16-bit data.
Image representative of range Product Details Remote I/O Adaptor This module acts as a communication gateway between a Remote I/O scanner module (not supplied) and digital or analogue I/O modules in 1747-asb Replacement All the comms LED's and the ladder seem happy, module status but no channel status lights on the second module and no data. The system returned: (22) Invalid argument The remote host or network may be down.
The plc is mounted on a panel with one main expansion board 10-slot with the AB SLC-500, one output card(dry relay), and six rtd input cards, and a scanner. How can I leave a product review? Publication 1746-UM022B-EN-P 1746-UM022B-EN-P - January 2005 Module Overview Side Label , operating and fault status of channels 0 to 7 Module Status LED Displays operating and fault status , module reads 1794-asb Manual What am I missing?
Please click here to register! The system returned: (22) Invalid argument The remote host or network may be down. The system returned: (22) Invalid argument The remote host or network may be down. More about the author Interpreting Error Codes . . . . . . . . . . . . . . . . . . . , Procedure. . . . . . . .
© Copyright 2017 downloadcallwave.com. All rights reserved.